1. Error Detection Method
When there is no communication within a 3-minute period from the outdoor unit. Or, judged an error when no reply comes from the outdoor unit.
2. Error Diagnosis
|1-1||Is/was the power to the outdoor unit cut off?||Yes||After turning the power on, wait three minutes|
|1-2||Is the indoor unit powered off?||Yes||Power on|
Indoor/ outdoor control line
|2-1||Is the indoor/outdoor operation line shorted, opened, grounded or has a wrong contact?||Yes||Correct the wiring|
|2-2||When the network of indoor/outdoor operation line was wired, was the (SHORT) setting of the terminal resistor switch on the outdoor control PC board set on multiple units (four or more)?||Yes||Normally the (SHORT) setting is just one unit.|
|2-3||Was a high voltage (over AC200V) applied in the indoor/outdoor operations line circuit?||Yes||3-2|
No. of Indoor Units
|3-1||Was the number of indoor units increased or decreased after auto address setting was complete?||Yes||3-2|
|3-2||Conduct checks prior to auto address setting.|
|3-3||Check the indoor unit addresses from the remote control’s detailed settings mode.
Is it Not Set (99), or is the indoor unit’s address duplicated?
Indoor unit control PC board
|4-1||Are the CHK pin and/or TEST pin on the indoor unit control PC board short-circuited?||Yes||Remove the short|
|4-2||Is the wireless remote controller and/or optional control PC board connected to on the indoor unit’s control PC board?||Yes||4-3|
|4-3||Disconnect the connector mentioned above on the control PC board of the indoor unit control PC board, and see whether the E04 goes off after several minutes. (When doing so, if two remote controllers are being used and the wireless remote controller is the main remote controller, set the other remote controller as the main.)||Yes||4-4|
|4-4||Replace all optional control PC board and/or wireless remote control parts including wiring.|
|4-5||Is the LED on the indoor unit control PC board blinking?||Yes||4-6|
|4-6||The nonvolatile memory (EEPROM) on the indoor unit’s control PC board is either not installed, improperly installed or the nonvolatile memory is faulty. Correct this or after replacing the nonvolatile memory, write model data to it in the remote control detailed settings mode.|
|4-7||Are all the remote controllers of the other indoor units connected to that outdoor unit displaying E04?||Yes||Replace the outdoor unit control board|
|No||Replace the indoor unit control board|